FIREBEAM-100M FIRE BARRIER CONNECTIONS
- Follow the installation manual and connect the barrier only with the power supply, proceed to configure the barrier. Once the installation and calibration of the barrier is completed, proceed with the following wiring for correct operation.
- The position of the REOL resistor corresponds to the end-of-line resistor of the control panel itself, which is connected between HJ1 and GZ1. For DMTech control panels, this value is read automatically and can be between 2K and 9K
- The position of the Fire resistor corresponds to the fire alarm resistor, it is connected between connector HJ2 and GZ1. For DMTech control panels, this value must be 1K.
FIREBEAM-100M barrier manual: FIREBEAM-100M
IMPORTANT NOTE: DO NOT MAKE THIS CONNECTION UNTIL THE BARRIER IS CONFIGURED AND CALIBRATED, OTHERWISE IT WILL NOT BE POSSIBLE TO CONFIGURE IT.