To activate the alarm output of Access Control SF-AC3011 when the door is opened irregularly (This manual is also suitable for controllers, changing the connection of the equipment) we have to follow the steps below:
1. The connections to be used are, on the one hand, that of the door sensor input (which is the one that will indicate the status of the door)
On the other hand, when the door sensor detects that the door has been irregularly opened, the alarm output of the device will be used through a link (here it is decided whether the output will be Normally Open or Normally Closed).
2. The next step is to configure the sensor input if we want it open or closed
In this example the normal state of the door contact is that it has to be open. When I close the contact on the two wires of the door sensor what the terminal receives (and can be checked in the software) is that the door has been opened irregularly and when it is reopened it indicates that it has returned to normal:
3. A link will be configured specifying that the alarm output must be activated when an anomalous door opening occurs:
Once the configuration has been saved, the alarm output will be activated each time this anomalous opening of the door occurs.